ATI Q46F/D Direct Fluoride Monitor
- Provides continuous measurement of free fluoride in potable water without sample conditioning
- Provides reliable measurements down to 0.1 PPM and as high as 1000 PPM
- Communication Options for Profibus-DP, Modbus-RTU, or Ethernet-IP
|Q46F/D||Direct fluoride monitor|| |
|Drop ships from manufacturer|
Many drinking water systems add fluoride to their water to help their residents prevent tooth decay. To achieve a fluoride concentration of about 1 PPM, a hydrofluorosilicic acid or sodium fluoride solution is metered into the process at a rate that is proportional to total plant flow. However, flow control problems may result in a loss of chemical feed or over-feed condition. An on-line fluoride monitor can provide reliable control of chemical addition for a consistent fluoride concentration.
ATI’s Model Q46F/D Fluoride Monitor provides continuous measurement of free fluoride concentration in potable water without sample conditioning. The system employs a fluoride sensitive ion selective electrode (ISE) which provides reliable measurements down to 0.1 PPM and as high as 1000 PPM. The system is designed for use in applications where the pH and conductivity of the water are relatively stable. Fluoride measurement applications with widely varying sample conditions may require a more sophisticated system employing automated sample conditioning such as ATI’s Q46F-AutoChem system.
Fluoride monitoring systems are easy to install, requiring a ¼” O.D. sample tube connected to a special flowcell provided as part of the system. Inlet flow must be regulated to 6 GPH (0.4 LPM) or less and should be stable. As an option, ATI can supply the fluoride monitoring system factory mounted on a panel containing all necessary flow controls and a visual flow indicator.
In The News
For most humans, mayflies seem like a nuisance, hovering over the waterways as we try to enjoy them. However, for anyone hoping to monitor the health of watersheds, mayflies are important aquatic species—and now, a digital version of the mayfly is helping some scientists keep an eye on the water. Research scientist Dr. Scott Ensign , who serves as Assistant Director of the Stroud Water Research Center , spoke to EM about how the digital mayfly technology developed.
“ Shannon Hicks is the engineer who started developing the Mayfly six or seven years ago,” explains Dr. Ensign.Read More
Time is of the essence when it comes to tracking algal blooms, and people everywhere are looking for solutions. In Florida, scientists from Florida Atlantic University Harbor Branch Oceanographic Institute (HBOI) recently trialed a solar-powered, algae-tracking sail boat developed by Navocean , Inc. Dr. Jordon Beckler of Florida Atlantic University (FAU) directs HBOI's Geochemistry and Geochemical Sensing Lab and spoke to EM about the trials and the boat.
"This boat is so amazing when you see it in action," remarks Dr. Beckler. "Navocean originally contacted me a few years back about a demonstration when I was over at my previous institution in West Florida, and we brainstormed some scenarios for employing the boat for harmful algae bloom monitoring.Read More
CICHAZ Biological Field Station Provides A Unique Educational and Research Experience in Mexico’s Huasteca Region
The story of the Centro de Investigaciones Científicas de las Huastecas "Aguazarca" (CICHAZ) Biological Field Station, a member of the Organization of Biological Field Stations ( OBFS ), starts with Dr. Gil Rosenthal, Professor of Biology and Chair of Ecology and Evolutionary Biology at Texas A &; M University . Rosenthal has worked in the Huasteca region of Mexico since 1994 and for years kept his research equipment at a local ranch/hotel with the dream of one day having a field station where he could run experiments with collaborators and students. Since 2005, Rosenthal has been the Co-Director of the field station along with his wife, Dr.Read More